GlobeCore engineers spent a week in Kenya (1 – 7 October) to commission a CMM-10 unit.
The unit was installed at Suswa substation and was used to purify electrical insulation oil and to fill transformers with the oil. The capacity of the CMM-10 in degassing, drying and filtration mode is 10 m3/hour.
With initial gas content below 10.5% and less than 100 ppm moisture, the parameters of processed oil are as follows:
- gas content below 0.1%;
- water content below 5 ppm;
- ISO 4406 purity -/14/12 or better.
The CMM-10 was operated for many hours at the substation and performed exactly as specified.
To place an order for this or another type of unit, please contact one of our sales managers.